Residential Reuse Project Los Angeles
|No, Of Rooms:||4|
|Products Used:||Pre treatment system to treat black water. Sand Polishing modules. holding tank. carbon filters and UV light.|
I - Water runs from Bio tech treatment system to sand polishing. From polishing the water runs to a 500 gallon holding tank. From there it is plumbed through 2 carbon filters and UV lights before returning back to the holding tank where it then disperses to a soak pit. Samples of final effluent will be taken and tested for re-use standard
II - If the quality of water from Phase I proves adequate then the system will run identical for phase II. However instead of water discharging to the soak pit, it shall now be dispersed to a sub surface drip system provided by "Geo Flow".
Samples of the final effluent will be taken and tested for reuse standard.
III - Again if the quality of water from phase II proves adequate then the system will run identical for phase II. However instead of water discharging to the soak pit, it shall now have an additional option of being dispersed to either the Geo Flow sub surface drip system
- By mounting UV Light and Carbon Filters to the outside wall of the house hase allowed the operator to maintain the system at ease and in a cleaner environment
- Room had been allowed to add any additional accessories to the system ....i.e. turbidity meter
- Help educate the local health departments on Bio techs technology and provide as much data as possible from systems that are already working out i the field
- This will help the authorities to understand the technology and capabilities that the Bio tech system provides to bring water to a reuse standard.